Flowmeters must be sized properly for each particular application, type of gas, gas pressure, and operating range. First, make sure that your flowmeter is calibrated for the specific gravity of the gas that you are metering. Check the label or the glass tube of the flowmeter or call the manufacturer to be sure. Second, operate the flowmeter only at the pressure for which it was calibrated. As an example, a variable-area flowmeter calibrated for 5,5 bar and reading 28,3 m³/h will really only be delivering 21,5 m³/h if it is operated at 2,8 bar. This is a 24% error! Third, for best accuracy and to allow room for adjustment, size the flowmeter so that your normal flow rate falls within 30%–70% of full scale. These three steps will help ensure that you have good control over your gas flows and, ultimately, your process.
Traditionally, high-pressure gas cylinders have been the supply mode for users in the low- to medium-volume range. This has left companies vulnerable to safety risks associated with moving cylinders and exposure to high pressure. Consolidating to a centralized microbulk system eliminates the need to handle cylinders and reduces the risk of product mix-up. Further benefits include decreased exposure to high-pressure containers and reduced traffic congestion with less frequent supplier deliveries. Air Products developed the microbulk supply option as a cost-effective, reliable alternative to high-pressure cylinders for nitrogen, argon, oxygen, and carbon dioxide supply. In addition to efficient and flexible storage systems, innovative piping solutions are available to help you have a smooth transition from cylinders to microbulk.